The heating system for your dorm is controlled by a boiler, which is natural gas fired. This boiler heats water that gets pumped through a Main Heating Valve (MHV) and then the radiators in each room at Denbigh.
There are temperature sensors (See Photo) in Room(s) 114, 115, 214, 215, 311 and 312. The energy management system averages the six sensor temperatures and “calls for heat” when the average is below set point (usually between 68°F and 72°F). On that call for heat, the MHV in Denbigh basement opens, sending hot water to the radiators in each room.
The rooms with temperature sensors can have a negative effect on the other rooms. For example, if the student in Room 114 (which has a sensor) opens the window, her sensor will cause the average temperature to drop and the heating system to respond by running the pump to warm the space. This sometimes causes an over-heating condition in the building. Conversely, if the student in Room 114 uses a space heater, her sensor will cause the average temperature to rise and the heating system to respond by shutting off the pump and likely making the rooms too cold.
Each student has a knob on her radiator that controls air flow. (See photo). This knob will not adjust the temperature of the air being distributed, but will increase or decrease the air flow. It is important to keep the space around your radiators clean and clear of personal items. Blocking air flow to the radiators can cause poor heat circulation.
**Note: The main heating valve closes any time the outside air temperature is above 60°F. This means that the heat is essentially “off” when the outside temperature reaches 60°F.
Between the hours of 11:00AM and 3:00PM Monday through Friday during the heating season, the target temperature range in all the dorms will be set back to 65-67°F.